|LIGHT SOURCE||41 X LED (TOTAL CIRCUIT 5W)|
|EMERGENCY DURATION||3 HOURS MIN.|
|MAINS VOLTAGE||230V ± 10%, 50/60Hz|
|MAINS CURRENT (MAX.)||40mA (max.)|
|RECHARGE PERIOD||LESS THAN 24 HOURS|
|CHARGE INDICATOR||INTEGRAL GREEN LED|
|CHANGOVER VOLTAGE||AS PER THE REQUIRMENTS OF BS EN 60598-2-22|
|TEMPERATURE RANGE||-10°C ~ +45°C|
|BATTERY||3.6V 1.5AH NICKEL CADMIOM|
|DIMENSIONS (mm)||353mm(W) X 110mm (H) X 70mm (D)|
LED’S normally off and battery ON automatic charge (LED “ON”) when AC supply is healthy. Solid state circuitry automatically switches lamp on when AC supply is interrupted.
LED’S normally ON, when the supply to LED is switched ON. The battery is ON automatic charge (LED “ON”). Lamp will switch ON or remain ON if AC supply is interrupted.
GREEN indicator lamp (LED) normally continuously “ON”
Sealed nickel cadmium rechargeable battery pack
Performance figures measured at 25°C
The status display can only be cleaned after the fault has been rectified, main voltage has been reapplied and a function test has been run.
RECOMMENDED ROUTINE TEST PROCEDURE :
The following test is designed to ensure the continued protection of your premised and occupant. Because of the possibility of a failure of the normal lighting supply occurring shortly. After a period of testing, all tests should, whenever possible, be undertaken at times of least risk, e.g. during day light hours
ONCE A DAY
Visual inspection of battery charge LED.
ONCE A MONTH
Each unit should be energized fro it’s battery for adequate time to ensure, by simulation of a failure of the normal lighting supply, the emergency mode is functioning correctly.
ONCE EACH YEAR
All units should be placed into emergency mode and checked that the duration provided by the battery meets the specified time period.
Can be supplied multi directional GREEN running man legend which shall conform to standard be EN50172. Four different legend of self-ahensive exit sign kit.